STATEMENT BY UGU DISTRICT MUNICIPALITY:
Improvements on the system: Seaslopes feed restored after a temporary repairs were done; however still need to get new 375 upvc line. Seaslopes picking up now and pumping to Kaisers and Ramsgate supply planned for tomorrow morning.
Gamalakhe: 600 still has no water; meter insert and plant strainet opened and checked no obstruction.
Northern system: Melville is dropping due to burst line but bypass opened. Woodgrange still not restored which indicate possible valve closure. Northern flows will be checked first.
Umzimkhulu reservoir and tower levels are above 70%; palm view and location 7 no water logged.
Margate CBD reservoirs 2A and 9A are building up and team dispatched to attend to no water.